Rittal CMC-III LCP: Water In/Out Temperature
|Distribution:||official part of Check_MK|
Note: This check is obsolete. The same sensors are handled by cmciii.temp
The rest of this man page is unchanged for legacy reasons:
This check monitors the temperature of the inflowing and outgoing water of
Rittal CMC-III LCP devices. No limits are set in the check, since limits
are configured in the Rittal device itself. The state given by the Rittal
device is taken as the state of the check as follows: If the Rittal device
returns OK, the check is OK. Otherwise the check is CRIT. Furthermore,
the lower and upper warning and critical limits configured in the device
are extracted and used as limimts for the temperature read from the device.
IN or OUT
The check will create the two items IN and OUT if it detects a proper device.