Generic UPS Device: Self Test
|Distribution:||official part of Check_MK|
This check monitors parameters related to the self test of UPS devices: the
result of the last self test and the last date of the self test run. The
check becomes CRIT if the test result is "doneError" or "aborted",
and WARN if the result is "doneWarning" or "noTestsInitiated". It also
has a WARN or CRIT state if the date of the last self test is more than
the warning or critical level ago.
The inventory process checks if the device has a system description OIDs
(.220.127.116.11.18.104.22.168.0) and if the name of this OID is known to the test. If
this is true the system is inventorized.